CAN/ULC-S PERIODIC INSPECTIONS AND TEST – DAILY AND MONTHLY. NOTE: Refer to Appendix D for examples of Inspection and Test Record. SCOPE. This Standard provides requirements for the inspection and testing of fire alarm systems and specifies the devices and functions to be inspected. 1 SCOPE This Standard prescribes requirements for the inspection and testing of fire alarm systems and specifies the devices and functions.
|Published (Last):||18 December 2018|
|PDF File Size:||17.12 Mb|
|ePub File Size:||20.7 Mb|
|Price:||Free* [*Free Regsitration Required]|
CAN/ULC-S Fire Alarm Annual Inspection Test Form
Identify zone, circuit number, or address. We provide expert inspection services to all makes and models of fire alarm and extinguishment systems. H Operation of voice paging does not interfere with initial inhibit time of alert I signal and alarm signal. Fire hose connection undamaged? Low water supervisory device inspected and tested.
Hydrostatic test at not less than Electrically Driven Pump Test Is the controller performing run cwn automatically? Audibility of alarm sounder checked? Low points in dry systems drained prior to freezing weather?
CAN/ULC-S536-04 Fire Alarm Annual Inspection Test Form
D Tested and confirmed operation of trouble relay. Audibility of alert, alarm and voice messages checked. Input circuit alarm and supervisory operation, including audible and visual indication R operates.
Weekly and Monthly Inspection Items Gauges on dry, pre-action and deluge systems in good condition? Powered independently of the fire alarm control, ulcc devices are normally not connected to it.
G Test to ensure lights function for a duration equal to design criteria? Alarm valves shall be inspected externally. Are all existing fire protection systems in service?
Cabinets easy to fully open? Swing x536 Racks – lubricate and ensure proper operation. Zones or module numbers if the system being tested is addressable must be recorded for each field device on the Individual Device Test Record ; End-of-Line devices resistors – these have to be listed along with their locations on the Individual Device Test Record and specific testing must be conducted that s356 their physical dismounting and re-installation; A536 data buss, power buss, and in-suite signal isolators – these have to be listed on the Individual Device Test Record including a reference to their actual location and some may require physical dismounting in order to affect a proper test; Smoke detector sensitivity readings – results must be recorded on the Individual Device Test Record.
Gaskets in place and in good condition? Combination multi-criteria detectors inspected and tested? Automatic Detectors other types inspected and tested for: Low temperature alarms in dry pipe, pre-action and deluge valve enclosure passed test?
Standards Council of Canada
Valve supervisory switches tested? Cap gaskets in place and in good condition? A copy should be maintained on the premises for examination by the Fire Marshal or Inspector at their request.
Most fire alarm systems employ zoned annunciators so that fire fighting personnel can be dispatched a536 the proper area of the building. Clean Cloudy Dirty Filter checked? S Input circuit supervision fault causes a trouble indication. Have someone standing by the panel so that they can cancel or silence any audible alarm quickly. Common visual trouble signal operates.
Ground fault tested on positive and negative initiates trouble signal. The fire signal receiving centre Acn certification number is: Abnormally frequent false tripping of dry-pipe valves? Tested for Operation results are recorded in the Device Test Record. The fire alarm system has: Electrolyte level in batteries is normal Tighten electrical connection as required?